Temperature Effect On Solar Power Generation
Solar Energy is one of the booming fields in the renewable energy sector. Due to effects of climate changes, Green energy summits across the globe have shown enthusiasm about solar energy policies. Land owners and industrial giants are willing to invest in the solar energy sector with an eye on profitable returns on investment and positive image created by reducing carbon footprint.
General belief is that more sun light gives more generation irrespective of weather condition, which is apparently true, but fact is that we cannot ignore the importance of environmental factors such as, temperature and wind speed that significantly influence solar energy generation. Generating solar power may seem facile but, when you start analysing each aspect of a solar plant one could find it quite riveting.
Generally, we expect good generation from solar panels during summer, because the insolation received over the panels will be higher. Analysis, shows it is not too beneficial; Plants sometimes struggle to meet expected generation numbers. Here temperature comes into the picture. While expecting higher generation with higher insolation we often ignore the fact of higher module temperatures which lead to lower than expected Solar energy generation.
Most commonly used PV module technology is Polycrystalline, and this material has a negative temperature coefficient. This means, with increase in temperature, generation efficiency of the module (which is typically 15-16%) will decrease. Typically, this temperature coefficient is around -0.4%/° C, this indicates with each degree rise from 25°C (which is the cell temperature at STC) the efficiency of module will reduce by 0.4%. Physics behind this phenomenon is that, with increase in temperature open circuit voltage decreases and reverse saturation current increases. Open circuit voltage(Voc) is the measure of amount of recombination in a Silicon cell or in other words it corresponds to the amount of forward bias, as Voc depends on saturation current and light generated current of solar cell. For a Si solar cell, saturation current becomes double with 10°C rise in temperature and brings down the open circuit voltage. The equation between these parameters is
According to climatic conditions in India, Polycrystalline modules are preferred in most of the regions. Hence, as per the working principle of polycrystalline modules one cannot expect higher generation numbers during high temperature days. Hence, temperature correction is important while evaluating generated units. Generally solar power plant performance is measured by a parameter called “Performance Ratio” (PR). This is the ratio of total generation for a time-period to maximum generation possible for the available DC load with available insolation during the same period.
One needs to apply temperature correction factor while calculating Performance Ratio of a plant. A theoretical approach to correct PR value is as follows:
PR % = (Energy AC) / (Energy DC STC X Insolation) % —— (1)
Temperature Corrected PR% = Normal PR (equation1) / (1 + µ(TCELL–25°C)) % ——(2)
µ is the Temperature coefficient provided by module manufacture
There is another method which NREL has suggested to calculate PR more accurately, but it requires average cell temperature for a whole year to calculate PR. The NREL suggested method is given below:
PR % = Normal PR (equation 1) / (1–µ (TCELL Avg–TCELL[i]))
TCELL Avg = Average module cell temperature
TCELL[i] = Temperature of Cell/Module at the time instant
Here we are giving one-month PR and corrected PR value for a 60MW plant (calculated by eqn 1 and 2), and the average difference is about 4% between Normal PR and Temperature corrected PR. This difference may vary month to month depending on weather condition.
From the above data we can infer that it is very much required to evaluate Solar Power plant performance according to the weather condition. In this study we have only considered the main aspect of weather i.e. Temperature, but other weather parameters like wind speed, wind direction, humidity have their own influence on the solar panel performance. Hence, if major influencers among these weather parameters are taken care off while evaluating generation units then it will give a more a realistic and accurate PR value.